- NEMA 4X
- Meets UL1203 & UL1638
- Built in flash
- Xenon strobe lamp
- Available in amber, blue, clear, green, purple (violet), and red
- two year warranty on power supply
- one year warranty on lamp
$1,948.90 – $2,290.77
|7120BEP–PMX||pendant mount, 3/4” hubs||120VAC|
|7120BEP–FMX||flange mount, 3/4” hubs||120VAC|
|7120BEP–WMX||wall mount, 3/4” hubs||120VAC|
|Lamp Type||6001 Xenon strobe lamp|
|Flash Rate||80 flashes per minute|
|Light Output||890 effective candlepower (ECP)*|
|Voltage and Amperage||120VAC 60 Hz draws 1.0A ( 1.7A max )|
|Power Supply Output 26 watts||20 joules per flash. 2,000,000 Peak Candlepower**|
|Operating Temperature||–40º C to +65º C|
|Temperature Code||T6 – All voltage and temperature ranges|
|Size and Weight||12” tall x 8.75” dia. x 13 lbs|
*ECP (Effective Candlepower) is the intensity that would appear to an observer if the light were burning steadily.
**Peak Candlepower is the maximum light intensity generated by a flashing light during its light pulse.
Visual signaling beacon shall be Tomar model number series 7120BEP or approved equal. The beacon shall be UL Listed Class I, Division 1, Groups C and D; Class II, Division 1, Groups E, F and G; and Class III for use in specified hazardous locations and /or combustible atmospheres as classified by the National Electric Code. The warning beacon shall have a 26 watt power supply and generate 20 joules per flash. Light intensity shall be 890 effective candlepower, and the light source shall be a plug-in field replaceable double-flash xenon strobe lamp operating at 80 flashes per minute. The warning signal must have built-in RFI filters to protect against radio interference and spike voltages. Beacon must have a built-in flash circuit, and voltage range shall 120VAC. Strobe beacon must meet UL 1203, and UL 1638, standards. Beacon must be rated NEMA 4X, with housing made of die cast high-strength copper-free aluminum alloy with baked powder epoxy finish, stainless steel hardware, O-ring sealed pre-stressed globe with double pitch acme threads for smooth assembly and ease of maintenance. Must include a Lexan® inner lens and tempered glass outer dome. The housing must be designed to accommodate a dome guard.